Welcome to the FMCA Motorhome Forums!
Register now to gain access to all of our features. Once registered and signed in, you will be able to create topics; post replies to existing topics; upload pictures; manage your profile; get your own private messenger; create blogs; and more. Sign up now! Already have an account? Sign in. This message will be removed once you are signed in.
I Want To Add An “Extend A Stay” Adapter To My Propane System.
Posted 02 November 2012 - 09:43 AM
I am thinking I want it on the right side so I can use it to also power my outside gas grill. What about going in the refrigerator access panel?
Allison 3000MH tran.
Towing a Honda Civic on a Acmey tow dolley.
Posted 02 November 2012 - 10:32 AM
Kay - Co-pilot
Allie - Beagle
Rascal - Beagle
2008 Tiffin Phaeton 40QSH
2012 Jeep Grand Cherokee Overland Toad
"Not All Who Wander Are Lost"
"It's never too late to have a happy childhood!"
Posted 02 November 2012 - 01:24 PM
Posted 19 November 2012 - 08:09 AM
Is this feasible and safe????
1997 Safari Serengeti M-4040
2002 VW Jetta TDI Toad & 2004 Ford Explorer Limited
Posted 19 November 2012 - 08:42 AM
Have you not been able to find a propane company who will fill your on-board tank?
Dianne and Brett Wolfe
1997 Safari Sahara 3540
Moderator, FMCA.com Forums
Chairman, FMCA Technical Advisory Committee
Member, FMCA Long-Range and Development Committee 2007-2009
Moderator, http://www.dieselrvclub.org/(FMCA chapter)
Posted 13 December 2012 - 12:07 PM
Currently on the left coast
Posted 13 December 2012 - 04:30 PM
Posted 18 May 2013 - 04:09 AM
I have attached the extend a stay system to my coach (Newmar Diesel Pusher) and connected to a 30 lb bottle, however my furnace will not operate? Am I doing something wrong?
Posted 18 May 2013 - 06:19 PM
Furnaces are very touchy to the amount of gas pressure it is receiving. Do your other gas appliances work? If yes, you might check the connections from the gas bottle to the extend a stay and make sure no thread tape or "pipe dope" is blocking the opening a little which could cause a partial clog and decrease the pressure enough to cause a problem with the furnace.
Next thing is I would make sure you turn the 30 lb tank on very slowly, turning it on fast with a 5' or longer hose between it and the regulator may cause the OPD valve inside the tank to think there is a leak and shut off the flow.
Pretty much all I can think of right now, hopefully others will chime in with some more ideas.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users