60 Amp Fairground Outlet
Posted 11 December 2012 - 11:02 AM
Is this correct, and if I make an adapter from 50 to 60 amps will I be able to use it without problems?
Posted 11 December 2012 - 11:45 AM
Would sure check it out with a voltmeter before plugging in.
If it looks like a 50 amp outlet:
Outer prongs are both HOT
Inner straight prong is NEUTRAL
Inner round is GROUND
Either outer to center straight or round= 120 VAC
Outer to outer= 240 VAC
Center straight to center round= 0 VAC
If it looks like a 30 amp outlet, RUN, FOREST, RUN.
If it is a 3 phase plug, RUN, FOREST, RUN.
Dianne and Brett Wolfe
2003 Alpine 38'
Moderator, FMCA.com Forums
Chairman, FMCA Technical Advisory Committee
Member, FMCA Long-Range and Development Committee 2007-2009
Moderator, http://www.dieselrvclub.org/(FMCA chapter)
Posted 11 December 2012 - 11:59 AM
Heres what I would do. I have 50 amp power cable for my coach and therefore I would plug into the 50 amp plug. I would then go to the GCs office and ask, "What is the 60 amp plug for?".
"Fair winds and Following Seas"
Herman & Bobbie Mullins, F302225
'02 Monaco Dynasty, 40-foot 400 HP ISL
Chevrolet Silverado (M & G air brakes)
U.S. Navy PR-3 1956 to 1964
Southern Region Vice President for Six-State Rally Association
Lone Star Chapter FMCA Past President
Stars of Texas
Rally in The Pasture
Posted 11 December 2012 - 12:42 PM
Posted 11 December 2012 - 01:12 PM
Thanks for your response. The only apparent difference was that the bottom pin was horizontal instead of vertical. There was, in fact, 120 vac on both outside legs. What about the phase - could it be different?
Posted 11 December 2012 - 01:25 PM
CERTIFICATE OF CONFORMANCE for link # 1
This is to certify that: 9049
The material shipped conforms to the requirements of
Product : HUBBELL HBL7303C AC Plug NEMA 18-60 Male
Description: Male Plug NEMA 18-60 Black and White Nylon, Angle, 4 Position. Rated for
120/208 volt, 60 amp, 4 pole, 4 wire, three phase. Accomodates .625-1.31 Inch cord
diameter. Straight Blade Plug. UL Listed.
This does not look like they should be used in RV Camp grounds, Lack of ground wire if someone who did not know what the wiring should be,(Not a Master Electrician) installed them.
Being a Fairgrounds these are for High Power 3 phase Motors used on rides !!!!
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users